Apply voltage to all charging systems so that the charging systems can come online (it can take 5 minutes for the charging system to come online and is ready as soon as the light turns green) (Note: do not connect the available data cables to the red terminals yet, this will come later )
Report to our helpdesk (+31 (0) 411 74 50 20) the charging point number that has come online, stating which pole should be set as master and which charging systems should be set as slave
After the charging systems have received the correct master or slave settings, the data cables can be connected to the red terminal
As a last step, the master charging system and the last slave must be fitted with a 120 ohm resistor. All charging systems between the master and the last slave should not have a resistor.
Maximum 9 slaves behind 1 master.
The recommended data cable is a can bus cable min CAT 5.
Data cable may only be looped through (no star network).